|Question: 06-33||Code Section: 7||Date:||
OBC 2006 Reference: 184.108.40.206.(1).
Question: Can a chair carrier's 2" vent connection have a urinal discharge into it ? Would it serve as a wet vent?
Interpretation: The majority of the Code Technical committee agree that according to 220.127.116.11.(1). a T fitting shall not be used except to connect a vent pipe. If the carrier had a “Y” connection and an accredited testing agency approval, the committee would then approve the design provided the urinal was not of the siphonic type.